|MAX. Flow:|| |
|Max Operating Temp:|| |
Sanitary Stainless Steel Self Suck Water CIP Pump
|Inlet/Outlet Size|| |
|Standard||3A DIN SMS|
The Pump is a asanitary side channel self priming pump, it's suitable for food processing,pharmacy and chemical industry. it is specially designed for pumping materials containing air or gas, and it can also be used for negative suction with prior priming as well as with filtration equipment.
It can be used with wine, oil, syrups,volatile products such as alcohol, acetone and other solvents, or with products at tem peratures close to boiling polint. However, the main use of this pump is for CIP return.
Design and features
This pump is composed of motor, pump shaft, mechanical clamping jacket, sanitary mechanical seal, connection support, rear plate impeller, pump shell, etc. It is return pump specially designed for CIP. It has the stainless steel protection cover used for protecting the motor, and the euqipment is supported by four adjustable feet.
Signle mechanical seal is standard, if you need double mechanical seal, please contact with us.
Max inlet pressure: 0.5 Mpa
Temperature range: -10℃ ~ 100℃
Single mechanical seal:
Hydraulic pressure: max. 0.1mpa
usually suits for -10℃ ~ 100℃
Contacting parts: AISI 316L or AISI 304
Other parts: AISI 304
Standard seal for pump head is silicone , mechanical seal o ring is FRM. EPDM or NBR is optional
Outside is shot blasting in satin finish
External is mirror polish at 0.4um, or shot blasting in satin finish
Installation Method and Place:
It is very necessary to check the following before installation:
The drive is in good condition.
Whether the on-site power supply is the same as the rated power on the motor nameplate.
Whether it meets the environmental conditions (avoid flammable and explosive environment or acid corrosion environment).
The installation foundation of the pump should generally be level and sufficient-strengthened ground. Install it as far as possible on the lowest position of the equipment, that is, at the position with the maximum head height.
The diameter of pump, pipe and the inlet and outlet of the pump should be the same, and the diameter of the inlet pipe should not be too small. When the diameter of the pipe is smaller than the diameter of the pump, adjust it with an eccentric reducer to shorten the diameter of the pipe so as to avoid formation of a gas leak. The outlet pipe diameter must not be too large either. When the outlet pipe diameter is larger than the pump outlet, try to extend it. Distance from the pump outlet to avoid overloading the pump motor.